Air Conditioning & Heating
Indoor Air Quality
- Air Conditioning
- Home Depot Partner
Minden, NV Air Conditioning, Heating and Home Services
Look, we’ll admit it, it can be a bit of a challenge getting comfortable in your home here in Minden. We understand because we’re locals here too. But we’re also professionals, so we can help you get the home comfort that you need with ease. There’s nothing worse than coming into a sizzling home here in the summer or a freezing cold home in the winter and waiting seemingly endlessly for your space to get to your desired temperature. We can help you sidestep the problems of defunct HVAC systems with the expertise of our team members. Contact us today to learn more.
We help homeowners improve the Comfort, Safety, Efficiency, and Health of their home. Call or click today to schedule HVAC services in Minden, NV.
Minden, NV Air Conditioning Services
Are you looking for great air conditioning services here in Minden? We’re in one of those areas where all the local HVAC contractors claim to specialize in air conditioning services. Your air conditioning services are important, so you want to really pour into the amenities that you have for this system. Choose professionals like ours, people who value their customers. Quality is the backbone of every service we perform.
Are you looking for better heating services in your home? Sometimes, you want to upgrade the way you heat your home, but you don’t necessarily know which system would be best for you. Your home heating doesn’t have to be difficult. You can trust our team to provide you with the best furnace, boiler, and radiant heating system services on the market. We repair, replace, maintain, and even install too.
Fireplace Installation and Service
If you’re lucky enough to have a fireplace in your home, you know what a luxury a system like this is, you also know that they can be a bit of a hassle to maintain. That’s why we’re here though. We’re always going to provide homeowners here in Minden with the best fireplace services around so that you can stay safe, sound, warm, and happy in your home. Come to us when you need service for traditional fireplaces, inserts, and even stove systems.
Indoor Air Quality Services
There really isn’t much that trumps your indoor air quality services when you’re talking home comfort. Your indoor air quality affects the efficacy of your HVAC system and your overall home health. If you need great indoor air quality services, you’re going to need to contact a professional to work on any of the IAQ systems in your home. We service air filtration systems, air purifiers, and whole-home humidifiers too. Get in touch today.
Home Performance Services
Are you looking for the right home performance services here in Minden? Trust us when we say that our services are the best in the area. We specialize in air sealing, ductwork services, duct cleaning, and even insulation services. Our team specializes in quality work without wasting your time so we’ll get in fast, find your weak points, and build your home back up so that you can enjoy optimal home comfort without the high price tag.
for Minden, NV
Our Reviews by City
Carson City, NV (9)
Dayton, NV (1)
Fernley, NV (8)
Gardnerville, NV (2)
Portola, CA (2)
Reno, NV (255)
Sparks, NV (106)
Sun Valley, NV (4)
Tahoe Vista, CA (1)
Truckee, CA (5)
VC Highlands, NV (1)
Verdi, NV (2)
Removal all of existing supply ductwork in crawl space. Installing new R-6 flexible duct, 12 runs total all the way to supply plenum! Completely sealed and strapped. New return plenum off of furnace. New 16" return flex ran to new cut in by main living room (high volume. (20x25x1) and also replacing old return grille with high volume 20x25x1. Once complete with new duct system install we will do a combustion balance on system to maximize performance of the old equipment. 100% Guaranteed Satisfaction with a Lifetime Warranty!!! $7,280.00
Near San Juan Cir, Minden, NV 89423
Furnace Diagnostic: Upon Arrival found unit trying to start up but nothing turning on burners. Found failed hot surface igniter and a very dirty unit that was in need of service/maintenance. Replaced hot surface igniter and everything kicked on normally. Furnace Maintenance: Checked operation of thermostat. Changed 1(20x30x1) return air filter and cleaned grille. Checked for gas and co leaks. Cleaned furnace housing, blower and burner compartments. Pulled and polished flame sensor. Checked capacitor mfd ratings 7.5 Checked amp draws on inducer motor and found inducer motor over amping and on last leg Checked combustion 7.9% oxygen and 23 ppm Static .75" w.c. Found return is undersized and needs to be dealt with in future Informed homeowner that unit is definitely on last leg considering the age of equipment. Average Life is 15-20 years and his equipment is 30 years old. Also informed he needs a CO detector!
Near Bridle Way, Minden, NV 89423
Upon arrival, homeowner informed me that right before he bought the house there was a big plumbing flood issue and that the restoration company took care of it before he bought it. Except for the air flow issues throughout home. I think that he thought that they fixed duct work during renovation 4 years ago. He informed me that there are hot/cold spots throughout the home and also lack of air flow! Started furnace in heat and checked static pressure on supply side .18" & return side reading .68" w.c. Which then Explained to him what static pressure means for comfort through out his home, efficiency and longevity of equipment. Found return was undersized at 16" duct but in OK condition. Went under home and found 4 ducts not even connected and insulation/liner was not even on just hanging. Found sagging ducts with dirt and debris. Refer to estimate!
Near San Juan Cir, Minden, NV 89423
Furnace Maintenance: Checked operation of thermostat. Changed 1(20x30x1) return air filter and cleaned grille. Checked for gas and co leaks. Cleaned furnace housing, blower and burner compartments. Pulled and polished flame sensor. CHECKED HOT SURFACE IGNITER AND FOUND BURNT OFF SILICONE AND WHITING. Cleared pressure ports and tubing. Checked amp draws on blower and inducer motor. CHECKED CAPACITOR R:10 A:8.2 MFD. CHECKED COMBUSTION 12.2% OXYGEN AND 14 PPM. Static total .53" w.c. Temp rise 52 degrees REPLACED FAILING HOT SURFACE IGNITER AND 10 MFD CAPACITOR. COMBUSTION AFTER BALANCE WAS 9.0% OXGEN AND 26 PPM. TESTED FURNACE
Near Fremont St, Minden, NV 89423
Furnace Maintenance: Checked operation of thermostat. Changed 1(20x30x1) return air filter and also cleaned grille. Checked for gas and co leaks. Cleared pressure ports and tubing. Pulled and polished flame sensor. CHECKED HOT SURFACE IGNITER AND FOUND BURNT OFF SILICONE AND WHITING. checked amp draws on blower and inducer motor. Checked capacitor mfd ratings 10. CHECKED COMBUSTION 14.8% OXYGEN AND 12PPM. static total .48" w.c. Temp rise 58 degrees. Replaced failing hot surface igniter and combustion after balance was 12.2% oxygen and 65ppm. Could not get combusrion any higher without popping high limit switch. Installed Lennox UV germicidal light to help with alllergens, bacteriaâ€™s, viruses and mold!
Near Skyline Dr, Minden, NV 89423